Laboratories for Metrology
The constant close control on Temperature is a fundamental requisite for dimensional metrology according to the ISO 1 International Standard that fixes the reference temperature at 20°C for geometrical specifications (GSS).
The requirements are various depending on the application fields, on measurements accuracy of coordinate measuring machines (CMM) and on geometrical parts to be conditioned.
Even if the requirements specify that it is not compulsory that all calibrations and tests for the acceptance of mechanical parts must be done at 20°C, it is indicated that a measurement done at a different temperature may lead to apply an offset on final results contributing to the increase of measure uncertainty.
Calibrations and measurements done with CMM (large bridge-type machines, bridge-type measuring machines and servo-driven gantry style machine, etc.) are performed in air conditioned rooms with variable air volumes depending on machines dimension, but always as same requisite is the importance to keep the at a constant temperature of 20°C and with a reasonably low percentage of relative humidity (%) to reduce at minimum level the apply of an offset and having more reliable and reproducible measurements.
Acceptable limits for temperature gradients are around ± 0,5°C, which has to be set in order to define clearly how much temperature could acceptably move from 20°C during the test activities without penalizing excessively the quality of measurements. For this reason it is important that the precision air conditioning system maintains the temperature under close control and relative humidity (%) higher threshold too through a constant regulation.
Branca Idealair offers three solutions for Metrology laboratories:
SOLUTION 1 : The Climatic Element - Branca Idealair
High accuracy measurements with the precision air conditioning handled from the "Climatic Element Branca Idealair" with a proper thermal insulation of laboratory followed by specialized technicians from S.T.A. Branca Idealair able to guarantee the thermo-hygrometric parameters below:
Select your "Laboratory cubic meters air volume (m3)" to get more information:
SOLUTION 2: CABINET
Solution 2 is provided by an insulated chamber with Climatic unit Type "CABINET" that ensures the following reference ambient parameters:
or for Electrical Metrology applications:
SOLUTION 3 : MEASURE BOX
Available various air volumes specified chosen by the customer the "Measure box" is the ideal solution to get an extremely satisfactory precision air conditioning of parts (for example commonly used for Johnson gauge blocks) inside a small air volume preliminary chosen by the customer and guaranteeing the tolerances here below:
Prof. Guglielmo M. Tino (Dipartimeto di Fisica e Astronomia and LENS Laboratory)
Università degli Studi di Firenze
Istituto Nazionale di Fisica Nucleare, Sezione di Firenze
POLO scientifico - Via Sansone 1 I-50019 Sesto Fiorentino (Firenze) ITALY
Tel.: +39 055 457-2034 (Office) - 2214 (Lab), - 2462 (Lab)
Fax.: +39 055 457-2121
"... In several occasions I had the opportunity to advice other colleagues about your excellent realization of the precision air conditioning system of our MAGIA laboratory; that was an essential element for the success of the MAGIA experiment whose goal was the accurate measurement of the gravitational constant G which is a fundamental physical constant of metrological interest. ..."
Dott. Vincenzo Greco (CNR Istituto nazionale di ottica)
Largo Enrico Fermi, 6 50125 Firenze (Italy)
Tel.: +39 055 2308271
Fax.: +39 055 2337755
"... As anticipated by phone call we perform temperature measures inside our conditioned room for a period of 3 hours with time sampling of 5 minutes. The data anlyses shows that in 1 hour the flunctuation of temperature values in correspondece to the average value is +/- 0,1 °C (measure uncertainty 2 sigma that represents for a normal distribution corresponds to a level of reliability of 95%) ... "